Supply voltage monitoring
- Emergency Power
- Renewable Energy
- Voltage monitoring
- Monitoring the supply voltage of an office complex to detect a power failure.
- If the supply voltage falls below the fixed threshold of 0.85 times the nominal voltage, the device switches off and enables the emergency power system and the emergency lighting through the relay output in systems that comply with VDE 0108-100 and VDE 0100-718.
- - Safe and reasonably priced solution
May I help you?
Can't find what you're looking for? Please don't hesitate to contact me.
This might be of interest for you
No entries found.
Catching the sun!
The most important but also basic task for a PV installation is to get the most solar energy converted by the modules. With just two inputs and NO CONTACTORS…
Der Energy Meter und Messwertumformer S9XM300A1000VM misst alle essenziellen elektrischen Parameter von Antrieben in der Automatisierungstechnik komplett…
With the TELE voltage monitoring device critical electrical states such as undervoltage, asymmetry and phase failure are easily detected.
Rotation direction monitoring for heat pumps
A heat pump should be protected against rotation in the wrong direction. If the phase sequence is incorrect, the pump must not be switched on. If a phase fails…
Energy measurement for wind generators and small hydropower plants
Energy measurement for wind generators and small hydropower plants S6XM50A1000VM und S9XM300A1000VM Wind turbines or small hydropower plants are confronted with…
Mains failure monitoring
The emergency lighting is activated in the event of a mains failure or undervoltage.