- Building Systems
- Centrifugal Pumps
- Emergency Power
- Heat Pumps
- Hydropower Plants
- Industrial Plant
- Liquid Waste Processing System
- Renewable Energy
- Safety Technology
- Ventilation Systems
- Wind Power
- ENYA/supply voltage
- In autonomously supplied commercial and building services systems, systems with long supply lines or weak energy supply (remote buildings), anomalies can often be detected in the supply voltage itself. With the TELE voltage monitoring device, critical, electrical states such as undervoltage, asymmetry and phase loss are easily detected. These are caused by the start-up of different building technology systems (e.g. air conditioning plants, ventilation plants, heat pumps or lifts) and detected and analysed by the E1YM480Y/277VS10.
- The E1YM480Y/277VS10 measures the voltage in all 3 phases and detects deviations from the set voltage thresholds. An internal timer is used to define how long a deviation can be tolerated and thus enables a delayed shut-down. In this way, brief deviations will not immediately trigger a switching procedure.
- Simple measurement through connection of the 3 phase voltages. The device is energy-saving (consumes less than 1 Watt), and supplies itself from the measuring circuit. The design is extremely compact, measuring 17.5 mm in width, and fits in any power distributor. The simple setting procedure allows any electrician to adjust the parameters of your system.
May I help you?
Can't find what you're looking for? Please don't hesitate to contact me.
This might be of interest for you
No entries found.
Electronic load shedding relay prevents overloads
TELE relais prevents operation of more than one high-load consumer at a time E1IM10AACL10 When running several electrical consumers simultaneously, such as…
Power failure monitoring CNC milling machine
In order to detect momentary power failures in a CNC machining center, the system is equipped with the TELE V2UF230V10 voltage-drop detector.
Monitoring of a fan motor for V-belt breakage or slippage.
Controlling electric heater elements and infrared lamps
The combination of OVP1 and the space saving thyristorstack TST1-230 is perfect for controlling IR lamps and fast reacting heaters.
Feed pump monitoring
The feed pump at a natural gas fuel station must be monitored for dry running. If no LNG is being pumped, the pump must be switched off.
The consistency of the material to be agitated should remain constant.