- Building Systems
- Centrifugal Pumps
- Emergency Power
- Heat Pumps
- Hydropower Plants
- Industrial Plant
- Liquid Waste Processing System
- Renewable Energy
- Safety Technology
- Ventilation Systems
- Wind Power
- ENYA/supply voltage
- In autonomously supplied commercial and building services systems, systems with long supply lines or weak energy supply (remote buildings), anomalies can often be detected in the supply voltage itself. With the TELE voltage monitoring device, critical, electrical states such as undervoltage, asymmetry and phase loss are easily detected. These are caused by the start-up of different building technology systems (e.g. air conditioning plants, ventilation plants, heat pumps or lifts) and detected and analysed by the E1YM480Y/277VS10.
- The E1YM480Y/277VS10 measures the voltage in all 3 phases and detects deviations from the set voltage thresholds. An internal timer is used to define how long a deviation can be tolerated and thus enables a delayed shut-down. In this way, brief deviations will not immediately trigger a switching procedure.
- Simple measurement through connection of the 3 phase voltages. The device is energy-saving (consumes less than 1 Watt), and supplies itself from the measuring circuit. The design is extremely compact, measuring 17.5 mm in width, and fits in any power distributor. The simple setting procedure allows any electrician to adjust the parameters of your system.
May I help you?
Can't find what you're looking for? Please don't hesitate to contact me.
This might be of interest for you
No entries found.
Wine press monitoring
In wine presses, phase sequence faults and phase failures cause serious problems and damage.
Controlling electric heater elements and infrared lamps
The combination of OVP1 and the space saving thyristorstack TST1-230 is perfect for controlling IR lamps and fast reacting heaters.
Conveyor belt monitoring
A conveyor belt must be stopped rapidly in the event of a blockage with small packages. However, unnecessary downtime must be avoided if at all possible.
Grapevine pest control
For pest control, a mechanical switch is actuated at each grapevine. The nozzle should then be activated for a certain time to spray the respective substance…
Pipe system cleaning
Chemical deposits are to be removed from pipe networks mechanically by means of different compressed air and water pressure impulses.
When the lights fail in public buildings (such as schools) because of undervoltage, the emergency lighting systems must be activated in publicly accessible…