Sensorless pump monitoring
- Power factor
- Data sheet:
- Three operating conditions should be monitored for a chemical pump:
* Dry running
* Mislaid input filter or no intake
* Lower density through heating of the medium
- The G4CM690V16ATL20 cosinus phi monitor from TELE reliably measures the power factor of the motor and switches the control output when it falls below a predefined level. A second switch value can be used as advance warning in order to prevent a fault.
- * Minimization of outages of the pumps through prompt shutdown
* Recognition of mislaid/worn filters
* Recognition that the medium is becoming warmer (density)
* No additional sensors needed* Simple wiring and simple settings
* Easy to retrofit
* Economical monitoring of aggressive, hot, explosive media
* Start-up conditions are hidden as defined
This might be of interest for you
No entries found.
Sewage plant rake drive
The goal is to monitor a sewage plant rake for overload, and to switch it off when it is blocked by large pieces of wood.
Waste incineration system screw conveyor
Shutdown of the screw conveyor in the event of overload.
Continuous operation detection
Preventing the destruction of a compressor due to continuous operation after an air hose becomes defective.
Dry running protection for submersible motor-driven pumps
Monitoring of household wells so that they are not pumped dry, and to ensure that the pump does not run dry.
Fluid level monitoring
When the pools at a waste water treatment plant are filled to a constant level, this causes undefined states for the float switches (a “flutter state”).
Fountain fill level
The fill level must be monitored in fountains so that the water pump can be activated when the water level is too low.