Sensorless pump monitoring
- Water & Waste
- Power factor
- Data sheet:
- Three operating conditions should be monitored for a chemical pump:
* Dry running
* Mislaid input filter or no intake
* Lower density through heating of the medium
- The G4CM690V16ATL20 cosinus phi monitor from TELE reliably measures the power factor of the motor and switches the control output when it falls below a predefined level. A second switch value can be used as advance warning in order to prevent a fault.
- * Minimization of outages of the pumps through prompt shutdown
* Recognition of mislaid/worn filters
* Recognition that the medium is becoming warmer (density)
* No additional sensors needed* Simple wiring and simple settings
* Easy to retrofit
* Economical monitoring of aggressive, hot, explosive media
* Start-up conditions are hidden as defined
May I help you?
Can't find what you're looking for? Please don't hesitate to contact me.
This might be of interest for you
No entries found.
Dry running protection for submersible motor-driven pumps
Monitoring of household wells so that they are not pumped dry, and to ensure that the pump does not run dry.
Monitoring of pumps & valves
The Watchdog relais E1ZMWt10 detects water flow pulses to make sure that pumps and valves work properly
Short circuit monitoring
Pumps are monitored with PTC resistors or thermal contacts. When PTC resistors are used, the sensor cable should be monitored for short circuits. The available…
Leak detection, defective pipes
V4LM4S30 24–240V AC/DC Artikel Nr.: 2104500 Leaks in water tanks or pipes for water, water-soluble liquids or cleaning lyes usually cause serious damage in…
Pump control to reduce water hammering in the pipe system
Christian P-4.0 with soft start and soft stop increases the water pressure in the pipe in a controlled way. The pump does not generate water hammering the pipes…
Prevention of filling a tank with air/monitoring a tanker at a minimum level.