Rotation direction monitoring for heat pumps
- Facility Management
- Heat Pumps
- Renewable Energy
- A heat pump should be protected against rotation in the wrong direction. If the phase sequence is incorrect, the pump must not be switched on. If a phase fails during operation, the heat pump should switch off, and a fault should be indicated.
- A voltage monitor monitors the phase sequence and phase failure. If the heat pump is connected incorrectly or if the sequence of phases changes during operation, the heat pump cannot be switched on, or is disconnected from the power supply immediately. Monitoring the asymmetry detects the failure of a phase and protects the heat pump against possible damage. Even when reverse voltage is generated when the motor continues to run on two phases.
- - Prevention of damage to the heat pump by reliable detection and shutdown in the event of an incorrect rotation direction or phase failure
- Prevention of unnecessary guarantee incidents in connection with damage caused by factors beyond the control of the operator
May I help you?
Can't find what you're looking for? Please don't hesitate to contact me.
This might be of interest for you
No entries found.
Automatic fan control of drying chamber
The monitoring relais E3IF500mAAC20 controls automatic start/stop of auxiliary drives.
Monitoring emergency lighting system
An undervoltage monitoring relay with a fixed switching threshold at 0.85% of the nominal voltage is needed for emergency lighting systems. Two changeover…
Door contact monitoring
Monitoring doors/door contacts at remote buildings (dock sheds) to detect unauthorised opening
Lift equipment service
A wide range of different control and supply voltages are used for conveyor and transport systems. The maintenance of expensive inventories of replacement parts…
Panel heating monitoring
Monitoring of panel heaters for failure.
Fountain fill level
The fill level must be monitored in fountains so that the water pump can be activated when the water level is too low.