Rotation direction monitoring for heat pumps
- Facility Management
- Heat Pumps
- Renewable Energy
- A heat pump should be protected against rotation in the wrong direction. If the phase sequence is incorrect, the pump must not be switched on. If a phase fails during operation, the heat pump should switch off, and a fault should be indicated.
- A voltage monitor monitors the phase sequence and phase failure. If the heat pump is connected incorrectly or if the sequence of phases changes during operation, the heat pump cannot be switched on, or is disconnected from the power supply immediately. Monitoring the asymmetry detects the failure of a phase and protects the heat pump against possible damage. Even when reverse voltage is generated when the motor continues to run on two phases.
- - Prevention of damage to the heat pump by reliable detection and shutdown in the event of an incorrect rotation direction or phase failure
- Prevention of unnecessary guarantee incidents in connection with damage caused by factors beyond the control of the operator
May I help you?
Can't find what you're looking for? Please don't hesitate to contact me.
This might be of interest for you
No entries found.
Lamp failure detection
Lamp failure detection in a lift car.
Controlling electric heater elements and infrared lamps
The combination of OVP1 and the space saving thyristorstack TST1-230 is perfect for controlling IR lamps and fast reacting heaters.
Operating range monitoring
Multiple fans driven by multiple motors are connected to a frequency converter. The internal monitoring systems in the frequency converter cannot recognise the…
The slippage or breakage of a V-belt should be signalled to a control room.
Emergency power monitoring
Phase failure for the operating theatre ventilation systems in hospitals is to be recognized as quickly as possible and the system is to be switched over to an…
Door contact monitoring
Monitoring doors/door contacts at remote buildings (dock sheds) to detect unauthorised opening