Automated roll gate/sliding gate control
- Product category:
- Power electronics
- Building Systems
- Facility Management
- Christian P-4.0
- Data sheet:
- Large motor driven roll or sliding gates for commercial building are heavy with a high mass to be accelerated or stopped. If you perform a DOL start of the motor you cause a very high inrush current too in the supply network and a huge mechanical stress for drive shaft and gearbox. In the case of stop, you also generate high stress for the mechanics, plus a lot of noise, especially for roll gates.
Another topic arises with sliding gates, which sometimes generate blocking situation by snow, dirt and cobble stones in the sliding area.
- The TELE-HAASE soft-starter CHRISTIAN P-4.0 with soft start/soft stop prevents the mechanics from heavy stress and the mains supply from peak current because of a continuous ramped acceleration and ramped breaking procedure. By stopping roll gates in the soft way reduces noise and mechanical stress dramatically. Reducing noise eliminates troubles in urban areas with neighbors. Reducing the mechanical stress, increases life time and reduces maintenance. The integrated forward/reverse control circuit makes it extremely easy to control both directions without a locking circuit or external components.
- The soft-starter CHRISTIAN P-4.0 with all components integrated (by-pass relay, soft start and softs stop, forward/reverse control and blocking protection) is extremely small, only 22,5mm width, and can be controlled by simple digital outputs without any additional electric components. With our soft starter you save space, components, maintenance during operation and therefore costs.
May I help you?
Can't find what you're looking for? Please don't hesitate to contact me.
This might be of interest for you
No entries found.
Re-cooling system monitoring
The overloading of the re-cooling systems in a data centre is prevented.
Monitoring of smoke extraction fans
Function monitors should be installed for smoke extraction fans that must run without motor protection, and possibly until they fail, in the event of a fire.
Building ventilation systems
Functional monitoring of V-belt-driven fans in technical building systems.
Mains failure monitoring
The emergency lighting is activated in the event of a mains failure or undervoltage.
The slippage or breakage of a V-belt should be signalled to a control room.
Rotation direction monitoring for heat pumps
A heat pump should be protected against rotation in the wrong direction. If the phase sequence is incorrect, the pump must not be switched on. If a phase fails…