Power source switchover
- Building Systems
- Facility Management
- When the voltage falls below 0.85 times the nominal voltage for longer than 0.5 seconds, the system must switch over from the normal power supply to the emergency power supply.
When the voltage exceeds 0.85 times the nominal voltage for at least one minute, the system may and should switch back to the normal power supply.
- The E3YF400VE20 0.85 has a fixed threshold of 0.85 the nominal voltage. If the mains voltage falls below this level, the monitoring relay sends the signal to switch to the emergency power supply.
The integrated time delay of one minute prevents the system from switching back and forth when the power supply fluctuates excessively over a longer period. One minute after the mains voltage returns to the normal level, the monitoring relay sends the signal to the system to switch back to mains voltage.
- - Both functions (monitoring and time delay) are combined in a single unit, which saves space
- Time savings during wiring, as only one device needs to be connected
May I help you?
Can't find what you're looking for? Please don't hesitate to contact me.
This might be of interest for you
No entries found.
Loading docklight control
The light on the loading dock and in the warehouse is often on all night even though no one needs it.
Building ventilation systems
Functional monitoring of V-belt-driven fans in technical building systems.
The slippage or breakage of a V-belt should be signalled to a control room.
Lift equipment service
A wide range of different control and supply voltages are used for conveyor and transport systems. The maintenance of expensive inventories of replacement parts…
Prevent elevator shaft from water damage
The TELE Pegelmonitor V4LM4S30 protects elevators and escalators from water water damage.
Safe grid separation for photovoltaic systems
Grid and system protection from TELE safely separates photovoltaic systems from the grid in the event of a fault. The unit is programmable, making it suitable…