Power source switchover
- Building Systems
- Facility Management
- When the voltage falls below 0.85 times the nominal voltage for longer than 0.5 seconds, the system must switch over from the normal power supply to the emergency power supply.
When the voltage exceeds 0.85 times the nominal voltage for at least one minute, the system may and should switch back to the normal power supply.
- The E3YF400VE20 0.85 has a fixed threshold of 0.85 the nominal voltage. If the mains voltage falls below this level, the monitoring relay sends the signal to switch to the emergency power supply.
The integrated time delay of one minute prevents the system from switching back and forth when the power supply fluctuates excessively over a longer period. One minute after the mains voltage returns to the normal level, the monitoring relay sends the signal to the system to switch back to mains voltage.
- - Both functions (monitoring and time delay) are combined in a single unit, which saves space
- Time savings during wiring, as only one device needs to be connected
May I help you?
Can't find what you're looking for? Please don't hesitate to contact me.
This might be of interest for you
No entries found.
Leak detection, defective pipes
V4LM4S30 24–240V AC/DC Artikel Nr.: 2104500 Leaks in water tanks or pipes for water, water-soluble liquids or cleaning lyes usually cause serious damage in…
Safe grid separation for photovoltaic systems
Grid and system protection from TELE safely separates photovoltaic systems from the grid in the event of a fault. The unit is programmable, making it suitable…
Automatic fan control of drying chamber
The monitoring relais E3IF500mAAC20 controls automatic start/stop of auxiliary drives.
Voltage dip detection
Very short voltage dips cause some components in a heating control system to fail, while others continue to function. This interrupts the control circuit, and…
LED lamp monitoring
LED lamps nowadays are widely used in buildings, industrial environment, plants and public places. The challenging task to monitor changes in the low lamp…
Monitoring of the operating state of the exhaust fan. The fan has a high starting current; this may not influence the monitoring and may not lead to a…