Power source switchover
- Other applications
- When the voltage falls below 0.85 times the nominal voltage for longer than 0.5 seconds, the system must switch over from the normal power supply to the emergency power supply.
When the voltage exceeds 0.85 times the nominal voltage for at least one minute, the system may and should switch back to the normal power supply.
- The E3YF400VE20 0.85 has a fixed threshold of 0.85 the nominal voltage. If the mains voltage falls below this level, the monitoring relay sends the signal to switch to the emergency power supply.
The integrated time delay of one minute prevents the system from switching back and forth when the power supply fluctuates excessively over a longer period. One minute after the mains voltage returns to the normal level, the monitoring relay sends the signal to the system to switch back to mains voltage.
- - Both functions (monitoring and time delay) are combined in a single unit, which saves space
- Time savings during wiring, as only one device needs to be connected
This might be of interest for you
No entries found.
Lamp failure detection
Lamp failure detection in a lift car.
Continuous operation detection
Preventing the destruction of a compressor due to continuous operation after an air hose becomes defective.
Voltage dip detection
Very short voltage dips cause some components in a heating control system to fail, while others continue to function. This interrupts the control circuit, and…
Panel heating monitoring
Monitoring of panel heaters for failure.
Monitoring of the operating state of the exhaust fan. The fan has a high starting current; this may not influence the monitoring and may not lead to a…
Sorting system lighting
Monitoring the lights in quartz and stone sorting systems for failure/faults.