Power source switchover
- Building Systems
- Facility Management
- When the voltage falls below 0.85 times the nominal voltage for longer than 0.5 seconds, the system must switch over from the normal power supply to the emergency power supply.
When the voltage exceeds 0.85 times the nominal voltage for at least one minute, the system may and should switch back to the normal power supply.
- The E3YF400VE20 0.85 has a fixed threshold of 0.85 the nominal voltage. If the mains voltage falls below this level, the monitoring relay sends the signal to switch to the emergency power supply.
The integrated time delay of one minute prevents the system from switching back and forth when the power supply fluctuates excessively over a longer period. One minute after the mains voltage returns to the normal level, the monitoring relay sends the signal to the system to switch back to mains voltage.
- - Both functions (monitoring and time delay) are combined in a single unit, which saves space
- Time savings during wiring, as only one device needs to be connected
May I help you?
Can't find what you're looking for? Please don't hesitate to contact me.
This might be of interest for you
No entries found.
Fan monitoring for paint or sandblast booth
The TELE load monitor GAMMA G2CU400V10AL10 recognizes faulty operating conditions of fan motors and triggers the delay timer.
Leak detection, defective pipes
V4LM4S30 24–240V AC/DC Artikel Nr.: 2104500 Leaks in water tanks or pipes for water, water-soluble liquids or cleaning lyes usually cause serious damage in…
Monitoring of the operating state of the exhaust fan. The fan has a high starting current; this may not influence the monitoring and may not lead to a…
Charge measurement for energy storage devices
Save and fully isolated measurement of DC energy packs VEO Series V4IA100A 24-240V AC/DC For battery power packs in energy storage devices, peak power systems…
Monitoring emergency lighting system
An undervoltage monitoring relay with a fixed switching threshold at 0.85% of the nominal voltage is needed for emergency lighting systems. Two changeover…
With the TELE voltage monitoring device critical electrical states such as undervoltage, asymmetry and phase failure are easily detected.