Power source switchover
- Other applications
- When the voltage falls below 0.85 times the nominal voltage for longer than 0.5 seconds, the system must switch over from the normal power supply to the emergency power supply.
When the voltage exceeds 0.85 times the nominal voltage for at least one minute, the system may and should switch back to the normal power supply.
- The E3YF400VE20 0.85 has a fixed threshold of 0.85 the nominal voltage. If the mains voltage falls below this level, the monitoring relay sends the signal to switch to the emergency power supply.
The integrated time delay of one minute prevents the system from switching back and forth when the power supply fluctuates excessively over a longer period. One minute after the mains voltage returns to the normal level, the monitoring relay sends the signal to the system to switch back to mains voltage.
- - Both functions (monitoring and time delay) are combined in a single unit, which saves space
- Time savings during wiring, as only one device needs to be connected
This might be of interest for you
No entries found.
Sorting system lighting
Monitoring the lights in quartz and stone sorting systems for failure/faults.
Burner process control
A temperature limiter is installed in the process controller of a burner. When it is triggered, a fault message should be sent and maintained after the power is…
Operating range monitoring
Multiple fans driven by multiple motors are connected to a frequency converter. The internal monitoring systems in the frequency converter cannot recognise the…
Building ventilation systems
Functional monitoring of V-belt-driven fans in technical building systems.
Monitoring of a cold store door
This is designed to prevent the cold store door from being open for too long while the cooling continues to run.
Monitoring emergency lighting system
An undervoltage monitoring relay with a fixed switching threshold at 0.85% of the nominal voltage is needed for emergency lighting systems. Two changeover…