Power source switchover
- Other applications
- When the voltage falls below 0.85 times the nominal voltage for longer than 0.5 seconds, the system must switch over from the normal power supply to the emergency power supply.
When the voltage exceeds 0.85 times the nominal voltage for at least one minute, the system may and should switch back to the normal power supply.
- The E3YF400VE20 0.85 has a fixed threshold of 0.85 the nominal voltage. If the mains voltage falls below this level, the monitoring relay sends the signal to switch to the emergency power supply.
The integrated time delay of one minute prevents the system from switching back and forth when the power supply fluctuates excessively over a longer period. One minute after the mains voltage returns to the normal level, the monitoring relay sends the signal to the system to switch back to mains voltage.
- - Both functions (monitoring and time delay) are combined in a single unit, which saves space
- Time savings during wiring, as only one device needs to be connected
This might be of interest for you
No entries found.
Furnace feed screw
Sequential control of 2 feed screws for a wood chip heating system.
Monitoring of the operating state of the exhaust fan. The fan has a high starting current; this may not influence the monitoring and may not lead to a…
Automated roll gate/sliding gate control
Soft-starter CHRISTIAN P-4.0 with soft start/soft stop prevents the mechanics of roll gates from heavy stress.
Fountain fill level
The fill level must be monitored in fountains so that the water pump can be activated when the water level is too low.
Re-cooling system monitoring
The overloading of the re-cooling systems in a data centre is prevented.
Monitoring of a cold store door
This is designed to prevent the cold store door from being open for too long while the cooling continues to run.