Power source switchover
- Building Systems
- Facility Management
- When the voltage falls below 0.85 times the nominal voltage for longer than 0.5 seconds, the system must switch over from the normal power supply to the emergency power supply.
When the voltage exceeds 0.85 times the nominal voltage for at least one minute, the system may and should switch back to the normal power supply.
- The E3YF400VE20 0.85 has a fixed threshold of 0.85 the nominal voltage. If the mains voltage falls below this level, the monitoring relay sends the signal to switch to the emergency power supply.
The integrated time delay of one minute prevents the system from switching back and forth when the power supply fluctuates excessively over a longer period. One minute after the mains voltage returns to the normal level, the monitoring relay sends the signal to the system to switch back to mains voltage.
- - Both functions (monitoring and time delay) are combined in a single unit, which saves space
- Time savings during wiring, as only one device needs to be connected
May I help you?
Can't find what you're looking for? Please don't hesitate to contact me.
This might be of interest for you
No entries found.
Monitoring of a cold store door
This is designed to prevent the cold store door from being open for too long while the cooling continues to run.
No flooding in the underground car park
The V4LM level monitor controls the entry of water into underground car parks and activates pumps to pump out the water as well as issue alarm signals as…
Building ventilation systems
Functional monitoring of V-belt-driven fans in technical building systems.
Fountain fill level
The fill level must be monitored in fountains so that the water pump can be activated when the water level is too low.
Continuous operation detection
Preventing the destruction of a compressor due to continuous operation after an air hose becomes defective.
Switch cabinet heating
Monitoring the switch cabinet heater for defects.