Operating range monitoring
- Facility Management
- Ventilation Systems
- cos phi
- Multiple fans driven by multiple motors are connected to a frequency converter. The internal monitoring systems in the frequency converter cannot recognise the failure of an individual fan.
- The permissible operating range of the electric motor for each fan is monitored with a cos phi monitoring unit using the “under” function. As soon as the cos phi leaves the acceptable range, for example because of a load reduction due to a defective V-belt or a dirty filter, the relay output is tripped, and the higher-level control system can recognise the fault.
- - Fast and low-cost monitoring, simple retrofit
- No sensor needed in the air channel – relevant for dust, heat and aggressive exhaust gases
- Lower maintenance requirements than for direct measurement in the air channel
- Measuring relay suitable for use with frequency converters
May I help you?
Can't find what you're looking for? Please don't hesitate to contact me.
This might be of interest for you
No entries found.
Lamp failure detection
Lamp failure detection in a lift car.
Sty ventilation system monitoring
The ventilation of a pigsty must be ensured. If the system fails, the animals could die.
Safe grid separation for photovoltaic systems
Grid and system protection from TELE safely separates photovoltaic systems from the grid in the event of a fault. The unit is programmable, making it suitable…
Switch cabinet heating
Monitoring the switch cabinet heater for defects.
Loading docklight control
The light on the loading dock and in the warehouse is often on all night even though no one needs it.
Monitoring emergency lighting system
An undervoltage monitoring relay with a fixed switching threshold at 0.85% of the nominal voltage is needed for emergency lighting systems. Two changeover…