Operating range monitoring
- Facility Management
- Ventilation Systems
- cos phi
- Multiple fans driven by multiple motors are connected to a frequency converter. The internal monitoring systems in the frequency converter cannot recognise the failure of an individual fan.
- The permissible operating range of the electric motor for each fan is monitored with a cos phi monitoring unit using the “under” function. As soon as the cos phi leaves the acceptable range, for example because of a load reduction due to a defective V-belt or a dirty filter, the relay output is tripped, and the higher-level control system can recognise the fault.
- - Fast and low-cost monitoring, simple retrofit
- No sensor needed in the air channel – relevant for dust, heat and aggressive exhaust gases
- Lower maintenance requirements than for direct measurement in the air channel
- Measuring relay suitable for use with frequency converters
This might be of interest for you
No entries found.
Panel heating monitoring
Monitoring of panel heaters for failure.
Passenger lift lighting
The function of the lighting in a passenger lift is monitored. If all lights fail, the lift may no longer be used.
Rotation direction monitoring for heat pumps
A heat pump should be protected against rotation in the wrong direction. If the phase sequence is incorrect, the pump must not be switched on. If a phase fails…
Door contact monitoring
Monitoring doors/door contacts at remote buildings (dock sheds) to detect unauthorised opening
Prevent elevator shaft from water damage
The TELE Pegelmonitor V4LM4S30 protects elevators and escalators from water water damage.
Building navigation lights
LED navigation lights on taller buildings and towers in the vicinity of airports should be monitored.