Operating range monitoring
- Facility Management
- Ventilation Systems
- cos phi
- Multiple fans driven by multiple motors are connected to a frequency converter. The internal monitoring systems in the frequency converter cannot recognise the failure of an individual fan.
- The permissible operating range of the electric motor for each fan is monitored with a cos phi monitoring unit using the “under” function. As soon as the cos phi leaves the acceptable range, for example because of a load reduction due to a defective V-belt or a dirty filter, the relay output is tripped, and the higher-level control system can recognise the fault.
- - Fast and low-cost monitoring, simple retrofit
- No sensor needed in the air channel – relevant for dust, heat and aggressive exhaust gases
- Lower maintenance requirements than for direct measurement in the air channel
- Measuring relay suitable for use with frequency converters
May I help you?
Can't find what you're looking for? Please don't hesitate to contact me.
This might be of interest for you
No entries found.
Sorting system lighting
Monitoring the lights in quartz and stone sorting systems for failure/faults.
Burner process control
A temperature limiter is installed in the process controller of a burner. When it is triggered, a fault message should be sent and maintained after the power is…
Voltage dip detection
Very short voltage dips cause some components in a heating control system to fail, while others continue to function. This interrupts the control circuit, and…
Panel heating monitoring
Monitoring of panel heaters for failure.
Passenger lift lighting
The function of the lighting in a passenger lift is monitored. If all lights fail, the lift may no longer be used.
Charge measurement for energy storage devices
Save and fully isolated measurement of DC energy packs VEO Series V4IA100A 24-240V AC/DC For battery power packs in energy storage devices, peak power systems…