Operating range monitoring
- Heating, ventilation and air conditioning
- Multiple fans driven by multiple motors are connected to a frequency converter. The internal monitoring systems in the frequency converter cannot recognise the failure of an individual fan.
- The permissible operating range of the electric motor for each fan is monitored with a cos phi monitoring unit using the “under” function. As soon as the cos phi leaves the acceptable range, for example because of a load reduction due to a defective V-belt or a dirty filter, the relay output is tripped, and the higher-level control system can recognise the fault.
- - Fast and low-cost monitoring, simple retrofit
- No sensor needed in the air channel – relevant for dust, heat and aggressive exhaust gases
- Lower maintenance requirements than for direct measurement in the air channel
- Measuring relay suitable for use with frequency converters
This might be of interest for you
No entries found.
Emergency power monitoring
Phase failure for the operating theatre ventilation systems in hospitals is to be recognized as quickly as possible and the system is to be switched over to an…
Sorting system lighting
Monitoring the lights in quartz and stone sorting systems for failure/faults.
Lamp monitoring in lifts
A current monitoring relay is needed for direct and rotary current with a measuring range from 10 mA to 10 A. The functions should include overcurrent and…
The slippage or breakage of a V-belt should be signalled to a control room.
Loading docklight control
The light on the loading dock and in the warehouse is often on all night even though no one needs it.
When the lights fail in public buildings (such as schools) because of undervoltage, the emergency lighting systems must be activated in publicly accessible…