Operating range monitoring
- Facility Management
- Ventilation Systems
- cos phi
- Multiple fans driven by multiple motors are connected to a frequency converter. The internal monitoring systems in the frequency converter cannot recognise the failure of an individual fan.
- The permissible operating range of the electric motor for each fan is monitored with a cos phi monitoring unit using the “under” function. As soon as the cos phi leaves the acceptable range, for example because of a load reduction due to a defective V-belt or a dirty filter, the relay output is tripped, and the higher-level control system can recognise the fault.
- - Fast and low-cost monitoring, simple retrofit
- No sensor needed in the air channel – relevant for dust, heat and aggressive exhaust gases
- Lower maintenance requirements than for direct measurement in the air channel
- Measuring relay suitable for use with frequency converters
May I help you?
Can't find what you're looking for? Please don't hesitate to contact me.
This might be of interest for you
No entries found.
Re-cooling system monitoring
The overloading of the re-cooling systems in a data centre is prevented.
Burner process control
A temperature limiter is installed in the process controller of a burner. When it is triggered, a fault message should be sent and maintained after the power is…
Continuous operation detection
Preventing the destruction of a compressor due to continuous operation after an air hose becomes defective.
The slippage or breakage of a V-belt should be signalled to a control room.
Emergency power supply
It must be ensured that the emergency power system is switched on within 30 ms when the lighting power supply fails.
Rotation direction monitoring for heat pumps
A heat pump should be protected against rotation in the wrong direction. If the phase sequence is incorrect, the pump must not be switched on. If a phase fails…