Operating range monitoring
- Facility Management
- Ventilation Systems
- cos phi
- Multiple fans driven by multiple motors are connected to a frequency converter. The internal monitoring systems in the frequency converter cannot recognise the failure of an individual fan.
- The permissible operating range of the electric motor for each fan is monitored with a cos phi monitoring unit using the “under” function. As soon as the cos phi leaves the acceptable range, for example because of a load reduction due to a defective V-belt or a dirty filter, the relay output is tripped, and the higher-level control system can recognise the fault.
- - Fast and low-cost monitoring, simple retrofit
- No sensor needed in the air channel – relevant for dust, heat and aggressive exhaust gases
- Lower maintenance requirements than for direct measurement in the air channel
- Measuring relay suitable for use with frequency converters
May I help you?
Can't find what you're looking for? Please don't hesitate to contact me.
This might be of interest for you
No entries found.
Automated roll gate/sliding gate control
Soft-starter CHRISTIAN P-4.0 with soft start/soft stop prevents the mechanics of roll gates from heavy stress.
Controlling electric heater elements and infrared lamps
The combination of OVP1 and the space saving thyristorstack TST1-230 is perfect for controlling IR lamps and fast reacting heaters.
Monitoring of smoke extraction fans
Function monitors should be installed for smoke extraction fans that must run without motor protection, and possibly until they fail, in the event of a fire.
Monitoring of the operating state of the exhaust fan. The fan has a high starting current; this may not influence the monitoring and may not lead to a…
Lamp failure detection
Lamp failure detection in a lift car.
Sorting system lighting
Monitoring the lights in quartz and stone sorting systems for failure/faults.