Operating range monitoring
- Heating, ventilation and air conditioning
- Multiple fans driven by multiple motors are connected to a frequency converter. The internal monitoring systems in the frequency converter cannot recognise the failure of an individual fan.
- The permissible operating range of the electric motor for each fan is monitored with a cos phi monitoring unit using the “under” function. As soon as the cos phi leaves the acceptable range, for example because of a load reduction due to a defective V-belt or a dirty filter, the relay output is tripped, and the higher-level control system can recognise the fault.
- - Fast and low-cost monitoring, simple retrofit
- No sensor needed in the air channel – relevant for dust, heat and aggressive exhaust gases
- Lower maintenance requirements than for direct measurement in the air channel
- Measuring relay suitable for use with frequency converters
This might be of interest for you
No entries found.
Safe grid separation for photovoltaic systems
Grid and system protection from TELE safely separates photovoltaic systems from the grid in the event of a fault. The unit is programmable, making it suitable…
Power source switchover
When the voltage falls below 0.85 times the nominal voltage for longer than 0.5 seconds, the system must switch over from the normal power supply to the…
Building navigation lights
LED navigation lights on taller buildings and towers in the vicinity of airports should be monitored.
Fountain fill level
The fill level must be monitored in fountains so that the water pump can be activated when the water level is too low.
When the lights fail in public buildings (such as schools) because of undervoltage, the emergency lighting systems must be activated in publicly accessible…
Furnace feed screw
Sequential control of 2 feed screws for a wood chip heating system.