Operating range monitoring
- Facility Management
- Ventilation Systems
- cos phi
- Multiple fans driven by multiple motors are connected to a frequency converter. The internal monitoring systems in the frequency converter cannot recognise the failure of an individual fan.
- The permissible operating range of the electric motor for each fan is monitored with a cos phi monitoring unit using the “under” function. As soon as the cos phi leaves the acceptable range, for example because of a load reduction due to a defective V-belt or a dirty filter, the relay output is tripped, and the higher-level control system can recognise the fault.
- - Fast and low-cost monitoring, simple retrofit
- No sensor needed in the air channel – relevant for dust, heat and aggressive exhaust gases
- Lower maintenance requirements than for direct measurement in the air channel
- Measuring relay suitable for use with frequency converters
May I help you?
Can't find what you're looking for? Please don't hesitate to contact me.
This might be of interest for you
No entries found.
Door contact monitoring
Monitoring doors/door contacts at remote buildings (dock sheds) to detect unauthorised opening
Power source switchover
When the voltage falls below 0.85 times the nominal voltage for longer than 0.5 seconds, the system must switch over from the normal power supply to the…
With the TELE voltage monitoring device critical electrical states such as undervoltage, asymmetry and phase failure are easily detected.
Monitoring of a cold store door
This is designed to prevent the cold store door from being open for too long while the cooling continues to run.
Building ventilation systems
Functional monitoring of V-belt-driven fans in technical building systems.
Lamp failure detection
Lamp failure detection in a lift car.