Operating range monitoring
- Facility Management
- Ventilation Systems
- cos phi
- Multiple fans driven by multiple motors are connected to a frequency converter. The internal monitoring systems in the frequency converter cannot recognise the failure of an individual fan.
- The permissible operating range of the electric motor for each fan is monitored with a cos phi monitoring unit using the “under” function. As soon as the cos phi leaves the acceptable range, for example because of a load reduction due to a defective V-belt or a dirty filter, the relay output is tripped, and the higher-level control system can recognise the fault.
- - Fast and low-cost monitoring, simple retrofit
- No sensor needed in the air channel – relevant for dust, heat and aggressive exhaust gases
- Lower maintenance requirements than for direct measurement in the air channel
- Measuring relay suitable for use with frequency converters
May I help you?
Can't find what you're looking for? Please don't hesitate to contact me.
This might be of interest for you
No entries found.
Leak detection, defective pipes
V4LM4S30 24–240V AC/DC Artikel Nr.: 2104500 Leaks in water tanks or pipes for water, water-soluble liquids or cleaning lyes usually cause serious damage in…
When the lights fail in public buildings (such as schools) because of undervoltage, the emergency lighting systems must be activated in publicly accessible…
No flooding in the underground car park
The V4LM level monitor controls the entry of water into underground car parks and activates pumps to pump out the water as well as issue alarm signals as…
Mains failure monitoring
The emergency lighting is activated in the event of a mains failure or undervoltage.
Re-cooling system monitoring
The overloading of the re-cooling systems in a data centre is prevented.
Building ventilation systems
Functional monitoring of V-belt-driven fans in technical building systems.