Emergency power supply
- Building Systems
- Facility Management
- Voltage monitoring
- Data sheet:
- It must be ensured that the emergency power system is switched on within 30 ms when the lighting power supply fails.
- By monitoring the supply voltage with the E3YF400, the emergency power system is activated within 20 ms in the event of a power failure.
- - Fulfilment of the legal requirement through rapid changeover to emergency power
May I help you?
Can't find what you're looking for? Please don't hesitate to contact me.
This might be of interest for you
No entries found.
Sty ventilation system monitoring
The ventilation of a pigsty must be ensured. If the system fails, the animals could die.
Monitoring emergency lighting system
An undervoltage monitoring relay with a fixed switching threshold at 0.85% of the nominal voltage is needed for emergency lighting systems. Two changeover…
Fountain fill level
The fill level must be monitored in fountains so that the water pump can be activated when the water level is too low.
Passenger lift lighting
The function of the lighting in a passenger lift is monitored. If all lights fail, the lift may no longer be used.
Re-cooling system monitoring
The overloading of the re-cooling systems in a data centre is prevented.
Controlling electric heater elements and infrared lamps
The combination of OVP1 and the space saving thyristorstack TST1-230 is perfect for controlling IR lamps and fast reacting heaters.