Emergency power supply
- Building Systems
- Facility Management
- Voltage monitoring
- Data sheet:
- It must be ensured that the emergency power system is switched on within 30 ms when the lighting power supply fails.
- By monitoring the supply voltage with the E3YF400, the emergency power system is activated within 20 ms in the event of a power failure.
- - Fulfilment of the legal requirement through rapid changeover to emergency power
May I help you?
Can't find what you're looking for? Please don't hesitate to contact me.
This might be of interest for you
No entries found.
Prevent elevator shaft from water damage
The TELE Pegelmonitor V4LM4S30 protects elevators and escalators from water water damage.
Furnace feed screw
Sequential control of 2 feed screws for a wood chip heating system.
Panel heating monitoring
Monitoring of panel heaters for failure.
Automated roll gate/sliding gate control
Soft-starter CHRISTIAN P-4.0 with soft start/soft stop prevents the mechanics of roll gates from heavy stress.
Building ventilation systems
Functional monitoring of V-belt-driven fans in technical building systems.
Emergency power monitoring
Phase failure for the operating theatre ventilation systems in hospitals is to be recognized as quickly as possible and the system is to be switched over to an…