Emergency power supply
- Building Systems
- Facility Management
- Voltage monitoring
- Data sheet:
- It must be ensured that the emergency power system is switched on within 30 ms when the lighting power supply fails.
- By monitoring the supply voltage with the E3YF400, the emergency power system is activated within 20 ms in the event of a power failure.
- - Fulfilment of the legal requirement through rapid changeover to emergency power
May I help you?
Can't find what you're looking for? Please don't hesitate to contact me.
This might be of interest for you
No entries found.
Panel heating monitoring
Monitoring of panel heaters for failure.
Monitoring emergency lighting system
An undervoltage monitoring relay with a fixed switching threshold at 0.85% of the nominal voltage is needed for emergency lighting systems. Two changeover…
Loading docklight control
The light on the loading dock and in the warehouse is often on all night even though no one needs it.
Operating range monitoring
Multiple fans driven by multiple motors are connected to a frequency converter. The internal monitoring systems in the frequency converter cannot recognise the…
Prevent elevator shaft from water damage
The TELE Pegelmonitor V4LM4S30 protects elevators and escalators from water water damage.
Burner process control
A temperature limiter is installed in the process controller of a burner. When it is triggered, a fault message should be sent and maintained after the power is…