Emergency power supply
- Building Systems
- Facility Management
- Voltage monitoring
- Data sheet:
- It must be ensured that the emergency power system is switched on within 30 ms when the lighting power supply fails.
- By monitoring the supply voltage with the E3YF400, the emergency power system is activated within 20 ms in the event of a power failure.
- - Fulfilment of the legal requirement through rapid changeover to emergency power
May I help you?
Can't find what you're looking for? Please don't hesitate to contact me.
This might be of interest for you
No entries found.
Building ventilation systems
Functional monitoring of V-belt-driven fans in technical building systems.
Monitoring of smoke extraction fans
Function monitors should be installed for smoke extraction fans that must run without motor protection, and possibly until they fail, in the event of a fire.
Manure removal systememergency stop
Monitoring of the manure removal system. The conveyor system must switch off when it is blocked by animals or a stoppage.
Rotation direction monitoring for heat pumps
A heat pump should be protected against rotation in the wrong direction. If the phase sequence is incorrect, the pump must not be switched on. If a phase fails…
Mains failure monitoring
The emergency lighting is activated in the event of a mains failure or undervoltage.
Re-cooling system monitoring
The overloading of the re-cooling systems in a data centre is prevented.