Emergency power supply
- Building Systems
- Facility Management
- Voltage monitoring
- Data sheet:
- It must be ensured that the emergency power system is switched on within 30 ms when the lighting power supply fails.
- By monitoring the supply voltage with the E3YF400, the emergency power system is activated within 20 ms in the event of a power failure.
- - Fulfilment of the legal requirement through rapid changeover to emergency power
May I help you?
Can't find what you're looking for? Please don't hesitate to contact me.
This might be of interest for you
No entries found.
Lamp failure detection
Lamp failure detection in a lift car.
Rotation direction monitoring for heat pumps
A heat pump should be protected against rotation in the wrong direction. If the phase sequence is incorrect, the pump must not be switched on. If a phase fails…
Furnace feed screw
Sequential control of 2 feed screws for a wood chip heating system.
Monitoring emergency lighting system
An undervoltage monitoring relay with a fixed switching threshold at 0.85% of the nominal voltage is needed for emergency lighting systems. Two changeover…
The slippage or breakage of a V-belt should be signalled to a control room.
Automatic fan control of drying chamber
The monitoring relais E3IF500mAAC20 controls automatic start/stop of auxiliary drives.