Emergency power supply
- Building Systems
- Facility Management
- Voltage monitoring
- Data sheet:
- It must be ensured that the emergency power system is switched on within 30 ms when the lighting power supply fails.
- By monitoring the supply voltage with the E3YF400, the emergency power system is activated within 20 ms in the event of a power failure.
- - Fulfilment of the legal requirement through rapid changeover to emergency power
May I help you?
Can't find what you're looking for? Please don't hesitate to contact me.
This might be of interest for you
No entries found.
LED lamp monitoring
LED lamps nowadays are widely used in buildings, industrial environment, plants and public places. The challenging task to monitor changes in the low lamp…
The slippage or breakage of a V-belt should be signalled to a control room.
Operating range monitoring
Multiple fans driven by multiple motors are connected to a frequency converter. The internal monitoring systems in the frequency converter cannot recognise the…
Panel heating monitoring
Monitoring of panel heaters for failure.
Passenger lift lighting
The function of the lighting in a passenger lift is monitored. If all lights fail, the lift may no longer be used.
Voltage dip detection
Very short voltage dips cause some components in a heating control system to fail, while others continue to function. This interrupts the control circuit, and…