Emergency power supply
- Building Systems
- Facility Management
- Voltage monitoring
- Data sheet:
- It must be ensured that the emergency power system is switched on within 30 ms when the lighting power supply fails.
- By monitoring the supply voltage with the E3YF400, the emergency power system is activated within 20 ms in the event of a power failure.
- - Fulfilment of the legal requirement through rapid changeover to emergency power
May I help you?
Can't find what you're looking for? Please don't hesitate to contact me.
This might be of interest for you
No entries found.
Charge measurement for energy storage devices
Save and fully isolated measurement of DC energy packs VEO Series V4IA100A 24-240V AC/DC For battery power packs in energy storage devices, peak power systems…
Lift equipment service
A wide range of different control and supply voltages are used for conveyor and transport systems. The maintenance of expensive inventories of replacement parts…
Building navigation lights
LED navigation lights on taller buildings and towers in the vicinity of airports should be monitored.
Monitoring of the operating state of the exhaust fan. The fan has a high starting current; this may not influence the monitoring and may not lead to a…
Monitoring emergency lighting system
An undervoltage monitoring relay with a fixed switching threshold at 0.85% of the nominal voltage is needed for emergency lighting systems. Two changeover…
Voltage dip detection
Very short voltage dips cause some components in a heating control system to fail, while others continue to function. This interrupts the control circuit, and…