Monitoring emergency lighting system
- Emergency Power
- Facility Management
- An undervoltage monitoring relay with a fixed switching threshold at 0.85% of the nominal voltage is needed for emergency lighting systems. Two changeover contacts are wanted for signalling.
- This device was used because it fulfils the VDE 0100-718 and VDE 0108-100 standards and is equipped with 2 changeover contacts.
- - Fixed threshold
- 2 contacts
- Fulfils VDE standard
May I help you?
Can't find what you're looking for? Please don't hesitate to contact me.
This might be of interest for you
No entries found.
Continuous operation detection
Preventing the destruction of a compressor due to continuous operation after an air hose becomes defective.
Mains failure monitoring
The emergency lighting is activated in the event of a mains failure or undervoltage.
Monitoring of smoke extraction fans
Function monitors should be installed for smoke extraction fans that must run without motor protection, and possibly until they fail, in the event of a fire.
Monitoring of a cold store door
This is designed to prevent the cold store door from being open for too long while the cooling continues to run.
Monitoring of the operating state of the exhaust fan. The fan has a high starting current; this may not influence the monitoring and may not lead to a…
When the lights fail in public buildings (such as schools) because of undervoltage, the emergency lighting systems must be activated in publicly accessible…