Building navigation lights
- Facility Management
- Current monitoring
- LED navigation lights on taller buildings and towers in the vicinity of airports should be monitored. A contact should be tripped when the power draw falls below the set power draw for a given lamp wattage. Different power draws from 10 mA to 5 A are needed.
- Different thresholds can be set in the current monitoring relay depending on the wattage of the lamps. Both in the ampere range and in the milliampere range.
- - One device for multiple configurable thresholds
- Lower inventory costs as a result
May I help you?
Can't find what you're looking for? Please don't hesitate to contact me.
This might be of interest for you
No entries found.
Power source switchover
When the voltage falls below 0.85 times the nominal voltage for longer than 0.5 seconds, the system must switch over from the normal power supply to the…
Continuous operation detection
Preventing the destruction of a compressor due to continuous operation after an air hose becomes defective.
Panel heating monitoring
Monitoring of panel heaters for failure.
Der Energy Meter und Messwertumformer S9XM300A1000VM misst alle essenziellen elektrischen Parameter von Antrieben in der Automatisierungstechnik komplett…
Monitoring emergency lighting system
An undervoltage monitoring relay with a fixed switching threshold at 0.85% of the nominal voltage is needed for emergency lighting systems. Two changeover…
When the lights fail in public buildings (such as schools) because of undervoltage, the emergency lighting systems must be activated in publicly accessible…